# Calculating cable weight

Discussion in 'General Electronics Chat' started by crossj3, Jul 13, 2018.

1. ### crossj3 Thread Starter New Member

May 10, 2018
11
0
Hi all

Currently installing a machine and need to know the cable weight required.

400v supply from a generator
Machine has total of 50 kw of motors on it.
The distance between the machine and power source is 35meters.

How do I calculate the cable size required?
I think it's 35mm squared cable. Am I right?
Thanks

2. ### BR-549 AAC Fanatic!

Sep 22, 2013
4,335
1,173
Do you mean cable or wire size? And it could depend on physical lay-out. What is the normal temp in that 35 meters?

Are you sure of that 400V figure? AC generator?

3. ### BR-549 AAC Fanatic!

Sep 22, 2013
4,335
1,173
Or do you mean the actual physical weight........as for stringing on poles?

4. ### crossj3 Thread Starter New Member

May 10, 2018
11
0
Basically looking for the wire size of each core.
Working in 20 degrees Celsius all the time .
Thanks

5. ### BR-549 AAC Fanatic!

Sep 22, 2013
4,335
1,173
I suggest you google "conductor vs current" and look at some wire charts in your language. It will be a large size. Don't forget to look at and figure out the voltage drop for 35 meters.

You might need to buy larger size than you realize.

Jul 18, 2013
16,778
4,982
I can see #1.0 AWG for motor loads, is this above or underground?
43mm2 to 33mm2.
Max.

Jul 18, 2013
16,778
4,982
How many actual motors, can they be started in sequence or at random?
Max.

8. ### dl324 AAC Fanatic!

Mar 30, 2015
7,845
1,878
That's 125 amps...
We call it gauge, not weight.

For power distribution, I'd use 0 AWG.

9. ### crossj3 Thread Starter New Member

May 10, 2018
11
0
There is 2 motors started one after another in sequence. One starts on star delta and the second one starts after

10. ### crossj3 Thread Starter New Member

May 10, 2018
11
0
Perfect Thanks. Some people call it weight here in Ireland

11. ### -live wire- Active Member

Dec 22, 2017
838
72
Um... why are you working with HV and extremely high power when you don't even know how to figure out the required wire gauge? You could easily be killed by a shock or arc blast.

12. ### Hymie Active Member

Mar 30, 2018
619
160
Cable with a cross sectional area of 35mm˄2 (1 AWG) is adequate for a current of up to 125A.

Given the cable length, and allowing a load margin you might consider 50mm˄2 (0 AWG) cable which can handle up to 160A.

13. ### crossj3 Thread Starter New Member

May 10, 2018
11
0
I don't do the wiring. I sold the machine. I just have to supply a power cable with it and want to know which one to buy. An electrician installs it.
I'm usually working with single phase and 12v.

14. ### -live wire- Active Member

Dec 22, 2017
838
72
Oh, ok.

Jul 18, 2013
16,778
4,982
Intended to be fed via conduit? Underground? Above ground?
Max.

16. ### crossj3 Thread Starter New Member

May 10, 2018
11
0
Overground. Mounted on wall brackets. Open to the air I suppose.

17. ### -live wire- Active Member

Dec 22, 2017
838
72
Also make sure there is good, thick, durable insulation. You don't want to go too cheap and have an arc blast or short. You will also need a lot thicker than you may think to have a safe margin. If there are any really HV transients, an arc could be established and maintained with the normal voltage. Even with good snubbers, there is always the chance a HVAC motor will create huge voltage spikes.

Jul 18, 2013
16,778
4,982
What about all the termination enclosures etc?
Max.

19. ### crossj3 Thread Starter New Member

May 10, 2018
11
0
On one end cable goes straight to generator poles.
On The other end the cable goes straight onto the main isolator switch in the machine panel. Enters the panel through a grommet and is bolted onto the isolator bars for each phase. Fused after the isolator.