Trying to fix a inop kitchen outlet in a 30 yr old mobile home. I removed the outlet and am only getting 60 volts between hot and neutral. Voltage between hot and ground is 120 volts. This is the first outlet in the circuit I believe. I am getting 120 volts when I check at the panel and put my meter on the affected 15 amp circuit breaker screw to the neutral bus and from the circuit breaker screw to the ground bus. Next I removed all three wires from the panel and with the kitchen outlet still unhooked I used a 20 ft jumper to go from the kitchen to the panel and checked for continuity. The neutral wire shows open while the hot and ground wires check good. Not sure where to go from here. I guess I am looking at running a new wire from the panel to the kitchen outlet unless anybody has any other ideas. Do not understand the 60 volt thing.