3 phase motor - calculating power
Mechanical guy here with little electrical knowledge.
I have the amps reading on each phase of a 50hp rated motor. The line voltage is know to be 460V. Don't know if it is a Y or Delta circuit (don't think it makes any difference).
Is the following an acceptable way to estimate the power usage of the drive?
Ip1 = 27
Ip2 = 28
Ip3 = 27
P drive = avg(27,28,27) * 460V * sqrt3 = 21.78 kW
Or am I way out in the left field?
The power for a three phase circuit is
Ptotal = sqrt3 * Vline * Iline * cos(theta) where
Vline is the line-to-line voltage, Iline is the current through a line (assmuming
the lines are balanced) and theta is the phase angle between the voltage and current.
The maximum power is when the phase angle between the voltage and current
is zero (cos(0) = 1). You should check to see if the motor specifies the
phase angle (or power factor).
(* jcl *)
or power = sum of power in each phase.
so it does matter to know if its a y or a delta.
or simply measure voltage across each phase(phase and neutral) or phase to phase current.
again for active power from drive u shud know abt the power factor.
also as already stated 50 HP shud be the full load power from the motor.
|calculating, motor, phase, power|
|Related Site Pages|
|Worksheet||Delta and Wye 3-phase circuits|
|Worksheet||Servo motor systems|
|Worksheet||AC motor theory|
|Textbook||Other specialized motors : Ac Motors|
|Textbook||Single-phase induction motors : Ac Motors|
|Textbook||Brushless DC motor : Ac Motors|
|Textbook||Stepper motors : Ac Motors|
|Textbook||Synchronous Motors : Ac Motors|
|Textbook||Polyphase motor design : Polyphase Ac Circuits|
|Thread||Thread Starter||Forum||Replies||Last Post|
|About AC supply||LDC3||General Electronics Chat||9||06-26-2013 11:02 PM|
|Split phase residential power and power factor||JamesL||The Projects Forum||12||07-04-2012 11:13 PM|
|is 220 V ac actily more efficent than 110V AC?||electronis whiz||Homework Help||12||05-29-2012 08:34 PM|
|Power requirement - 3 phase or single phase?||Tdawgg||General Electronics Chat||7||05-21-2012 05:15 AM|
|3 phase - bridge rectifier input/output power||Skeebopstop||General Electronics Chat||3||03-16-2009 02:51 AM|