All About Circuits Forum how to calculate 3 phase breaker size with given single phaee load amperes
 User Name Remember Me? Password
 Register Blogs FAQ Members List Today's Posts Search Today's Posts Mark Forums Read

 General Electronics Chat Discussion forum for general chat about anything electronics related, including asking questions about material in the All About Circuits E-book, Worksheets, and Videos.

#1
12-13-2012, 09:22 AM
 XEB New Member Join Date: Dec 2012 Posts: 1
how to calculate 3 phase breaker size with given single phaee load amperes

i want to calculate the size of a 3 phase main breaker of a workshop which has all single phase industrial sockets with total current of 2125 Amp.

40 sockets of 30Amps 40*30=1200
35 sockets of 20 Amps 35*20=700
15 sockets of 15 Amps 15*15=225
=2125Amps

what load distribution should i do?
and what would be the 3 phase main breaker size?
#2
12-13-2012, 12:10 PM
 Dodgydave Senior Member Join Date: Jun 2012 Location: Liverpool,UK. GMT Posts: 1,744

Well if your using single phase sockets then you need to be using single phase breakers, as the sockets will have to be evenly distributed across all 3 phases to balance the loads.

Also if you work on the fact that all the sockets wont be used all the time, and work on 75% rule that will be
2125A * 75% is 1600 amps approx over 3 phases gives approx 530 amps per phase THATS A LOT OF POWER !!!

Have you got that?
__________________
NECESSITY IS THE MOTHER OF INVENTION !

Last edited by Dodgydave; 12-13-2012 at 12:17 PM.
#3
12-13-2012, 12:33 PM
 gerty Senior Member Join Date: Aug 2007 Location: Tennessee GMT -5 Posts: 899

Quote:
 Also if you work on the fact that all the sockets wont be used all the time, and work on 75% rule that will be 2125A * 75% is 1600 amps approx over 3 phases gives approx 530 amps per phase THATS A LOT OF POWER !!!
In most cases that's true!
But he hasn't told us the application yet, if it's some sort of factory most of them may very well be on at the same time.

XEB: you need to give us more information, are these individual circuits going to machines that will be running most of the time?
Or are they going to recepticle circuits in a mall where not much of anything will be plugged in/turned on?

Last edited by gerty; 12-17-2012 at 04:55 PM.

 Tags amperes, breaker, calculate, load, phaee, phase, single, size

 Related Site Pages Section Title Worksheet AC network analysis Worksheet Superposition theorem Worksheet AC power Worksheet Series and parallel AC circuits Textbook Three-phase Y and Delta configurations : Polyphase Ac Circuits Textbook Three-phase power systems : Polyphase Ac Circuits Textbook Single-phase power systems : Polyphase Ac Circuits Worksheet Voltage divider circuits Worksheet Overcurrent protection Textbook Fuses : Physics Of Conductors And Insulators

 Similar Threads Thread Thread Starter Forum Replies Last Post strantor General Electronics Chat 8 09-19-2012 04:52 AM Talmadge General Electronics Chat 2 12-21-2008 02:56 AM kittyprincess66 The Projects Forum 16 07-16-2007 05:29 PM straw Homework Help 10 05-15-2007 03:47 PM shmerd General Electronics Chat 3 05-21-2005 01:59 PM

 Thread Tools Display Modes Linear Mode

 Posting Rules You may not post new threads You may not post replies You may not post attachments You may not edit your posts BB code is On Smilies are On [IMG] code is On HTML code is Off Forum Rules
 Forum Jump User Control Panel Private Messages Subscriptions Who's Online Search Forums Forums Home Electronics Forums     General Electronics Chat     The Projects Forum     Homework Help     Electronics Resources Software, Microcomputing, and Communications Forums     Programmer's Corner     Embedded Systems and Microcontrollers     Computing and Networks     Radio and Communications Circuits and Projects     The Completed Projects Collection Abstract Forums     Math     Physics     General Science All About Circuits Commmunity Forums     Off-Topic     The Flea Market     Feedback and Suggestions

All times are GMT. The time now is 02:42 PM.