All About Circuits Forum split phase power
 User Name Remember Me? Password
 Register Blogs FAQ Members List Today's Posts Search Today's Posts Mark Forums Read

 General Electronics Chat Discussion forum for general chat about anything electronics related, including asking questions about material in the All About Circuits E-book, Worksheets, and Videos.

#1
10-28-2004, 09:24 AM
 shmerd New Member Join Date: Oct 2004 Posts: 2

I would love to find a clear explanation. Is the power coming into my house single phase(2 110 lines in phase with each other)? split phase (2 110 line 180 out of phase)? If B, why is it refered to as single phase? I believe it is B or the two legs of 220 would read 0 volts? If someone could get back to me I would appreciate it! If there is a good online resource please let me know. This website calls split phase, single phase without giving any explanation.
#2
10-28-2004, 04:00 PM
 Perion Junior Member Join Date: Oct 2004 Posts: 43

Quote:
 Originally posted by shmerd@Oct 28 2004, 04:24 AM I would love to find a clear explanation.* Is the power coming into my house single phase(2 110 lines in phase with each other)? split phase (2 110 line 180 out of phase)? If B, why is it refered to as single phase? I believe it is B or the two legs of 220 would read 0 volts? If someone could get back to me I would appreciate it!* If there is a good online resource please let me know.* This website calls split phase, single phase without giving any explanation. Quoted post
Confusion can exist because of our definitions. Your home's incomming power is both split phase and single phase. They aren't mutually exclusive types. There a pretty good explanation with good diagrams here at http://www.allaboutcircuits.com/vol_2/chpt_10/1.html

In the summary it says:
Quote:
 Power systems in American households and light industry are most often of the split-phase variety, providing so-called 120/240 VAC power. The term "split-phase" merely refers to the split-voltage supply in such a system. In a more general sense, this kind of AC power supply is called single phase because both voltage waveforms are in phase, or in step, with each other. The term "single phase" is a counterpoint to another kind of power system called "polyphase"...
Even this could be a bit confusing because of the statement about split phase having "both voltage waveforms in phase, or in step, with each other". Refer to the diagram below.

If you connected a dual trace oscope's probes' gnds to the Neutral (center tapped wire) and put one probe on phase A and the other on phase B the waveforms would be 180 degrees out of phase. When A peaks positive B peaks negative. So how is it that the A-Neutral and B-Neutral voltages are said to be "in phase"? [Of course, it makes no sense to ask about the phasing of A-B - any voltage is always in phase with itself.]

The author explains that instead of supplying your house from the grounded center tapped transformer ("split phase") secondary you could substitue two series connected 120 vac single phase generators (synchronized and in phase ) and ground their tie point and have exactly the same system. They must be sychronized in phase since if they were otherwise their voltages would buck or cancel (a little like connecting batteries in series but opposite directions). Yet, if you choose the tie point (where gen 1 connects to gen2) as a measurement reference for your oscope, the other two leads supplying phases A and B in your panel would display waveforms 180 degrees out of phase, just like before. This out of phase characteristic is nothing more than the result of your choice of reference for the waveforms - you are measuring "from" the mid-point "out toward" the two opposite polarities of the winding.

The bottom line is this: electrically speaking (vs. some arbitray place we may choose for a measurement reference) the voltages across the two secondary portions are in phase. They don't buck or cancel but are series aiding - their voltages add directly with no phase angle to contend with. This is just the result of tapping a single winding right in its center point. Nothing mysterious happens. So you have a single phase (vs. some other multi-phase system like a closed delta three phase, etc.), split phase system (the secondary single phase winding is split in two, but still connected, parts by center tapping it).

Don't know if this helped or made things worse :blink:

Perion
__________________
&quot;Everything is what it is, but nothing is what it seems&quot;
- Jules Vernes
#3
10-30-2004, 08:32 PM
 shmerd New Member Join Date: Oct 2004 Posts: 2

Quote:
#4
05-21-2005, 01:59 PM
 macssam New Member Join Date: May 2005 Posts: 1

Quote:
 Originally posted by shmerd@Oct 30 2004, 09:32 PM Quoted post
I have read "shmerd's" article about single phase

is their a way to hook up European single phase 220-240 Volt devices
to operate in the US - I have tried without success

US 240V devices (air-condition) work O.K. connecting to European single phase 220-240

thanks
-sam- [SIZE=7]

 Tags phase, power, split

 Related Site Pages Section Title Video Lecture Transformers (Part 1) - Inductors,Capacitors,Transformers Textbook Single-phase induction motors : Ac Motors Textbook Tesla polyphase induction motors : Ac Motors Textbook Three-phase transformer circuits : Polyphase Ac Circuits Textbook Harmonics in polyphase power systems : Polyphase Ac Circuits Textbook Three-phase power systems : Polyphase Ac Circuits Textbook Single-phase power systems : Polyphase Ac Circuits Textbook Winding configurations : Transformers Textbook Special transformers and applications : Transformers Textbook Rectifier circuits : Diodes And Rectifiers

 Similar Threads Thread Thread Starter Forum Replies Last Post AutoNub General Electronics Chat 15 02-24-2012 01:01 AM andy24691 Homework Help 1 02-27-2011 12:03 AM andy24691 Homework Help 1 02-20-2011 04:54 AM E-book Correction Split Phase power Bill_Marsden Feedback and Suggestions 0 12-30-2009 05:37 PM Skeebopstop General Electronics Chat 3 03-16-2009 02:51 AM

 Thread Tools Display Modes Linear Mode

 Posting Rules You may not post new threads You may not post replies You may not post attachments You may not edit your posts BB code is On Smilies are On [IMG] code is On HTML code is Off Forum Rules
 Forum Jump User Control Panel Private Messages Subscriptions Who's Online Search Forums Forums Home Electronics Forums     General Electronics Chat     The Projects Forum     Homework Help     Electronics Resources Software, Microcomputing, and Communications Forums     Programmer's Corner     Embedded Systems and Microcontrollers     Computing and Networks     Radio and Communications Circuits and Projects     The Completed Projects Collection Abstract Forums     Math     Physics     General Science All About Circuits Commmunity Forums     Off-Topic     The Flea Market     Feedback and Suggestions

All times are GMT. The time now is 03:08 PM.